If you have a private well water system, your pressure switch is an integral component. The pressure switch tells the pump that delivers water to your home when to turn on and off. When the pressure in the system drops to a preset low setting (commonly known as the cut-on pressure) the contacts on the switch will close and the pump will turn on. When the pressure in the system rises to the preset high setting (commonly known as the cut-off pressure) the contacts on the switch will open and the pump will turn off . Pressure switches can be wired to work with 115 or 230 volts.
Caution! Electricity can be VERY DANGEROUS especially if you are inexperienced. Always use caution when working with electricity and TURN OFF POWER SUPPLY/CIRCUIT BREAKERS when testing components or making any adjustments within the electrical system. If you are not 100% confident you can perform any of these tests safely, call a professional.
With basic electrical knowledge, a pressure switch can be installed and wired with a few tools and materials.
Tools and material required:
screwdriver, wire strippers, pliers or similar, teflon tape
forked connectors, crimps, permanent marker
- Turn off power to the pump at the main panel.
- Test the wiring from the main panel to ensure that the power is off.
- Drain all water pressure from the system via a hose bib on the tank tee or nearest faucet.
- If you are replacing an old switch, remove existing wires and remove the old switch from the system.
- Secure the new switch to the jet pump or install on the piping of the existing submersible well pump system. Use teflon tape on the pressure switch inlet to prevent leaks. Click here to see video: How to Apply Teflon Tape the RIGHT Way
- Remove the cover of the new pressure switch with pliers and set aside. A wiring diagram is normally found on the inside of the cover.
- Loosen (do not remove) the screws on the pressure switch terminal with a screwdriver by turning in a counterclockwise direction.
- Feed wires from the pump motor and main power supply through the openings on either side of the switch.
- Attach the pump motor wires to the two terminals in the center marked “M” or “Load” (T1/T2). Attach the ground wire to the green ground screw.
- Attach the power supply from the main breaker to the outside terminals marked “Line” (L1/L2). Attach the ground wire to the green ground screw.
- Re-install the switch cover and reconnect the power.
- Test the pressure switch for several cycles to ensure that it is working properly.
If you need any further assistance or want help you may always call us at R.C Worst and we will be more than happy to help you! Call 855-329-4519 or visit our website. https://www.rcworst.com/
Here are some more helpful links you may be interested in
How to adjust a Pressure Switch Video
Square D Pressure Switch Video
Low Water Pressure Cutout Switch Video
Products you may be interested in:
Square D Pressure Switches
RCW Stainless Steel Pressure Tank Tee Assembly